Thank you for signing up for alerts.
1.1* Scope. A.1.1 NFPA13D is appropriate for protection against fire hazards only in one- and two-family dwellings and manufactured homes. Residential portions of any other type of building or occupancy should be protected with residential sprinklers in accordance with NFPA 13 or in accordance with NFPA 13R. Other portions of such buildings should be protected in accordance with NFPA 13 or NFPA 13R as appropriate for areas outside the dwelling unit. The criteria in this standard are based on full-scale fire tests of rooms containing typical furnishings found in residential living rooms, kitchens, and bedrooms. The furnishings were arranged as typically found in dwelling units in a manner similar to that shown in Figure A.1.1(a), Figure A.1.1(b), and Figure A.1.1(c). Sixty full-scale fire tests were conducted in a two-story dwelling in Los Angeles, California, and 16 tests were conducted in a 14 ft (4.3 m) wide mobile home in Charlotte, North Carolina. Sprinkler systems designed and installed according to this standard are expected to prevent flashover within the compartment of origin where sprinklers are installed in the compartment. A sprinkler system designed and installed according to this standard cannot, however, be expected to completely control a fire involving fuel loads that are significantly higher than average for dwelling units [10 lb/ft2 (49 kg/m2)] and where the interior finish has an unusually high flame spread index (greater than 225) when tested in accordance with ASTM E 84, Standard Test Method for Surface Burning Characteristics of Building Materials, or ANSI/UL 723, Standard for Test for Surface Burning Characteristics of Building Materials. (For protection of multifamily dwellings, see NFPA 13 or NFPA 13R.) ****INSERT FIGURE HERE**** FIGURE A.1.1(a) Bedroom. ****INSERT FIGURE HERE**** FIGURE A.1.1(b) Manufactured Home Bedroom. ****INSERT FIGURE HERE**** FIGURE A.1.1(c) Living Room. 1.1.1 This standard shall cover the design, installation, and maintenance of automatic sprinkler systems for protection against the fire hazards in one- and two-family dwellings and manufactured homes. 1.1.2 This standard shall not provide requirements for the design or installation of water mist fire protection systems, which are not considered fire sprinkler systems and are addressed by NFPA 750. 1.1.3 This standard shall be based on the concept that the sprinkler system is designed to protect against a fire originating from a single ignition location.
NFPA 13D is a residential sprinkler design standard focused on one- and two- family dwellings and manufactured homes. The intent is to provide an affordable sprinkler system in homes while maintaining a high level of life safety.
Requirements address automatic sprinkler system design, installation, and maintenance including numerous issues such as component listing, hydrostatic tests, sprinkler temperature ratings, design documentation, and hydraulic calculations.
Stakeholder Perceptions of Home Fire Sprinklers
Find a code or standard
© National Fire Protection Association (NFPA) 2016