Receive e-mail updates on this document
Thank you for signing up for alerts.
1.1* Scope. A.1.1 The following is a suggested procedure for determining the Code requirements for a building or structure: (1) Determine the occupancy classification by referring to the occupancy definitions in Chapter 6 and the occupancy Chapters 12 through 42. (See 6.1.14 for buildings withmore than one use.) (2) Determine if the building or structure is new or existing. (See the definitions in Chapter 3.) (3) Determine the occupant load. (See 7.3.1.) (4) Determine the hazard of contents. (See Section 6.2.) (5) Refer to the applicable occupancy chapter of the Code, Chapters 12 through 42. [See Chapters 1 through 4 and Chapters 6 through 11, as needed, for general information (such as definitions) or as directed by the occupancy chapter.] (6) Determine the occupancy subclassification or special use condition, if any, by referring to Chapters 16 and 17, daycare occupancies; Chapters 18 and 19, health care occupancies; Chapters 22 and 23, detention and correctional occupancies; Chapters 28 and 29, hotels and dormitories; Chapters 32 and 33, residential board and care occupancies; Chapters 36 and 37, mercantile occupancies; and Chapter 40, industrial occupancies, which contain subclassifications or special use definitions. (7) Proceed through the applicable occupancy chapter to verify compliance with each referenced section, subsection, paragraph, subparagraph, and referenced codes, standards, and other documents. (8) Where two or more requirements apply, refer to the occupancy chapter, which generally takes precedence over the base Chapters 1 through 4 and Chapters 6 through 11. (9) Where two or more occupancy chapters apply, such as in a mixed occupancy (see 6.1.14), apply the most restrictive requirements. 1.1.1 Title. NFPA 101, Life Safety Code, shall be known as the Life Safety Code®, is cited as such, and shall be referred to herein as “this Code” or “the Code.” 1.1.2 Danger to Life from Fire. The Code addresses those construction, protection, and occupancy features necessary to minimize danger to life from the effects of fire, including smoke, heat, and toxic gases created during a fire. 1.1.3 Egress Facilities. The Code establishes minimum criteria for the design of egress facilities so as to allow prompt escape of occupants from buildings or, where desirable, into safe areas within buildings. 1.1.4 Other Fire-Related Considerations. The Code addresses other considerations that are essential to life safety in recognition of the fact that life safety is more than a matter of egress. The Code also addresses protective features and systems, building services, operating features, maintenance activities, and other provisions in recognition of the fact that achieving an acceptable degree of life safety depends on additional safeguards to provide adequate egress time or protection for people exposed to fire. 1.1.5* Considerations Not Related to Fire. The Code also addresses other considerations that, while important in fire conditions, provide an ongoing benefit in other conditions of use, including non-fire emergencies. A.1.1.5 Life safety in buildings includes more than safety from fire. Although fire safety has been the long-standing focus of NFPA 101, its widely known title, Life Safety Code, and its technical requirements respond to a wider range of concerns, including, for example, crowd safety. 1.1.6 Areas Not Addressed. The Code does not address the following: (1)*General fire prevention or building construction features that are normally a function of fire prevention codes and building codes A.1.1.6(1) This Code is intended to be adopted and used as part of a comprehensive program of building regulations that include building, mechanical, plumbing, electrical, fuel gas, fire prevention, and land use regulations. (2) Prevention of injury incurred by an individual due to that individual’s failure to use reasonable care (3) Preservation of property from loss by fire
The Life Safety Code is the most widely used source for strategies to protect people based on building construction, protection, and occupancy features that minimize the effects of fire and related hazards. Unique in the field, it is the only document that covers life safety in both new and existing structures
Provisions are included for all types of occupancies, with requirements for egress, features of fire protection, sprinkler systems, alarms, emergency lighting, smoke barriers, and special hazard protection.
Find a code or standard
Customer Support: Help
Codes and Standards: Complete list Purchase Free Access National Fire Code Subscription Service (NFCSS)
On the Web: Blogs Buyers' Guide Electric Vehicle Safety Training Fire Adapted Communities Fire Prevention Week Fire Sprinkler Initiative Firewise
NEC® Buyers' Guide nec connect Sparky the Fire Dog®