Receive e-mail updates on this document
Thank you for signing up for alerts.
1.1* Scope. 1.1.1 This code shall apply to the design, installation, operation, and maintenance of compressed natural gas (CNG) and liquefied natural gas (LNG) engine fuel systems on vehicles of all types and for fueling vehicle (dispensing) systems and associated storage, including the following: (1) Original equipment manufacturers (OEMs) (2) Final-stage vehicle integrator/manufacturer (FSVIM) (3) Vehicle fueling (dispensing) systems A.1.1 Natural gas is a flammable gas. It is colorless, tasteless, and nontoxic. It is a light gas, weighing about two-thirds as much as air. As used in the systems covered by this standard, it tends to rise and diffuses rapidly in air when it escapes from the system. Natural gas burns in air with a luminous flame. At atmospheric pressure, the ignition temperature of natural gas–air mixtures has been reported to be as low as 900°F (482°C). The flammable limits of natural gas–air mixtures at atmospheric pressure are about 5 percent to 15 percent by volume natural gas. Natural gas is nontoxic but can cause anoxia (asphyxiation) when it displaces the normal 21 percent oxygen in air in a confined area without adequate ventilation. The concentrations at which flammable or explosive mixtures form are much lower than the concentration at which asphyxiation risk is significant. NFPA 704, Standard System for the Identification of the Hazards of Materials for Emergency Response, rating is as follows: (1) Health — 0 (2) Flammability — 4 (3) Reactivity — 0 (4) Special — None Cryogenic fluids are gases that have been liquefied by having their temperature brought below –130°F (–90°C). They are typically stored at low pressures in vacuum jacketed containers. Some of the potential hazards of cryogenic fluids are the following: (1) Extreme cold that freezes or damages human skin on contact and can embrittle metals (2) Extreme pressure resulting from rapid vaporization of the fluid during a leak or release of the cryogenic fluid (3) Asphyxiation resulting from a release of the cryogenic fluid that vaporizes and displaces air Personnel handling cryogenic fluids should use the protective clothing proscribed on the material safety data sheet (MSDS). This clothing typically includes heavy leather gloves, aprons, and eye protection. 1.1.2 This code shall apply to the design, installation, operation, and maintenance of liquefied natural gas (LNG) engine fuel systems on vehicles of all types, to their associated fueling (dispensing) facilities, and to LNG to CNG facilities with LNG storage in ASME containers of 70,000 gal (265 m3) or less. 1.1.3 Vehicles and fuel supply containers complying with federal motor vehicle safety standards (FMVSSs) covering the installation of CNG fuel systems on vehicles and certified by the respective manufacturer as meeting these standards shall not be required to comply with Sections 5.4, 5.8, 5.9, and 5.10 and Chapter 6 (except Sections 6.9, 6.11, 6.12, 6.13, and 6.14). 1.1.4 This code shall include marine, highway, rail, off-road, and industrial vehicles. 1.1.5 Vehicles that are required to comply with applicable federal motor vehicle safety standards covering the installation of LNG fuel systems on vehicles and that are certified by the manufacturer as meeting these standards shall not be required to comply with Chapter 9, except 9.12.8. 1.1.6 Where conflicts occur between provisions of this code and referenced codes and standards, the provisions of this code shall apply. 1.1.7 Where, in any specific case, different sections of this code specify different materials, methods, or other requirements, the most restrictive shall govern. 22.214.171.124 Where there is a conflict between a general requirement and a specific requirement, the specific requirement shall be applicable. 1.1.8 Manufacturer specifications shall equal or surpass the applicable requirements of this code.
Find a code or standard
Customer Support: Help
Codes and Standards: Complete list Purchase Free Access National Fire Code Subscription Service (NFCSS)
On the Web: Blogs Buyers' Guide Electric Vehicle Safety Training Fire Adapted Communities Fire Prevention Week Fire Sprinkler Initiative Firewise
NEC® Buyers' Guide nec connect Sparky the Fire Dog®